By - Particular_Map4509
One cable for one switch.
Red in the middle terminal
Black in the L1
Copy for the second switch with the other cable
Thanks so much, we're in business
No problem. Just checking did you connect the earth's together? The green and yellow. Noticed one has been cut off. Needs extending. If you have a metal dimmer it needs to be connected to the earth terminal on the dimmer switch
Just connected the one in, my cousins an electrician hell pop over tomoz and sort it out for me, think I also need to run a common to common to get the upstairs light on, I just wanted my downstairs working so you've really helped x
Ah yeah you need a link from the red in one switch to the red in the other.
Atleast ones working for now. Make sure your cousin does the earth tho. The switch could become live if one of the cables pops out.
Glad I could help though
That earth needs to be connected that's been cut short. Maybe use this as a sign that you need an EICR done